The chilled water cooled unit shall utilise the building available cooling medium, managing and deliver the cooling to the desire destination.
The chilled water coil shall be in an “A” frame arrangement to allow maximum coil surface in a small cabinet. The large faced coil shall be constructed with 1/2″ O.D. copper tube with 12 fins per inch of corrugated aluminum. Chilled water flow shall be controlled by a 3-way modulating valve for accurate and economical temperature control and dehumidification. Air bypass shall be provided to prevent saturated air from being introduced into the conditioned space.
The brochure as per below link